Siemens products may only be used for the applications described in the catalog The SITRANS FUE energy calculator has been developed for Siemens. Fine Controls are the official Technology partner for the Siemens instrumentation product range type FUE, Inline Ultrasonic Energy Meters, In Stock. Dec 4, Siemens Industry Automation Division introduces the Sitrans FUE thermal energy calculator, designed for use in hot water, chilled water.
|Published (Last):||26 February 2014|
|PDF File Size:||7.48 Mb|
|ePub File Size:||4.66 Mb|
|Price:||Free* [*Free Regsitration Required]|
The date and time remain actual but none of the measuring functions work, incl. Dimension Drawings Dimension drawings Page 50 Operation hardware 6. Display LCD off to save power and returns to basic display menu when button is pressed again. Temperature sensors are of the same pair. Technical Support If you have any technical questions about sjemens device described in these Operating Instructions and do fuue950 find the right answers, you can contact Technical Support: Typically, integrator is mounted on a wall or in a panel.
LCD off to save power and returns to basic display menu when button is pressed again.
Add-on Output And Input Modules “active” when installed. In case of deviating environmental conditions, energy meter has to be remounted regularly for service. Figure S – User sealing 3. Value of flowmeter pulse output is the same as value of energy meter pulse input.
SITRANS FUE – Automation Technology US – Siemens
Page 27 Connecting 5. Page 33 M-Bus-repeater or M-Bus-master. Functions and settings can be checked via display menus 3 and 4 and freely programmed using a software tool and the IrDA interface. Error is used as a warning.
SIEMENS SITRANS FUE OPERATING INSTRUCTIONS MANUAL Pdf Download.
Enter text from picture: Got it, continue to print. Page 6 Power supply Page 70 Appendix A. Don’t show me this message again.
The two slots for extension modules are shown in figures below. Please talk to your local Siemens contact or follow the return procedures sienens Siemens Flow Instruments described in chapter: In 1 Pulse 1 In 2 Pulse 2 counter counter 6.
They are intended for trained personnel and therefore do not include basic working steps.
Scope of delivery may vary depending on selections at ordering. Page 44 4 sec. Table of Contents Add to my manuals Add. Fe950 flowmeters 7me portable flowmeter pages. Connect shield to grounding at flowmeter. Lithium Batteries The label seal on the calculator see figures Page 49 must not be damaged! To print the manual completely, please, download it.
Flowmeter must be mounted in accordance with the instructions given in the relevant flowmeter operating instructions. Installation Of Device Typically, integrator is mounted on a wall or in a panel. Carefully slide plug onto board.
SIEMENS SITRANS FUE950 – ENERGY CALCULATOR
By pressing ‘print’ suemens you will print only current page. SW-tool Leak detection water meter at Disables: Page 21 Flowmeter must be mounted siemeens accordance with the instructions given in the relevant flowmeter operating instructions.
Month loop Display menu loops The various loops will show the following information: Gue950 2 resistors must be mounted between terminals 57 and 58 in the MAG terminal socket. Proper transport, storage, installation, assembly, commissioning, operation and maintenance are required to ensure that the products operate safely and without any problems.
Appendix Appendix Conformity to guidelines Declaration of conformity Siemens hereby declares that this product meets the essential requirements of the following guidelines: The functions and settings of the outputs can be freely programmed using a software tool and the IrDA interface, e.
Return Procedures Waste industrial batteries are accepted back by Siemens or by the local Siemens representative. Page 46 Operation hardware 6.
Sensors in forward and return lines must fit right to bottom of sensor pockets. A damaged seal will result in immediate invalidation of the factory warranty and calibration. A number of heat meters can be connected to a control centre. Catalog process instrumentation http: For more details, please contact Siemens Flow Instruments. Power Supply Options If no mains supply is connected, a back-up battery in the mains unit provides the power supply.